This article explain detailed procedure to calculate numerical value of a capacitor's capacitance to be connected with an Inductive load like induction motor to improve power factor from one value to other given value.

Capacitor calculation or capacitance calculation for a capacitor bank to improve power factor is very important topic for an electrical engineer. Capacitor bank help to reduce reactive power. Here is one numerical problem on capacitor or capacitance calculation for an induction motor.

Here is a Numerical Problem : -

A single phase 220 volts, 50 Hz, motor takes a supply current of 50 Amperes at a power factor of 0.5 lagging. The motor power factor has been improved to 0.9 lagging by connecting a condenser in parallel. Calculate the capacitance of the capacitor required ?

Solution : -

Motor Type : - 1 Phase, Induction Motor,

Voltage Applied : - 220 volts,

Current from Supply : - 50 Amp,

Supply Frequency : - 50 Hz,

Current Power Factor =cos Φ=0.5 ( lagging ),

Φ = cos^{-1}0.5=60^{˚}.

Active Component of current, say I_{a} = I * cos Φ = 50 * 0.5 = 25 Amp,

One thing you must remember regarding power factor improvement

Since the voltage also same so only current will be changed after power factor improvement. Hence only total current will be changed but active component will be same i.e. 25 Amp.

Tan Φ = tan 60 = 1.732,

Reactive component of current, say I_{r1} = I tan Φ = 25 * 1.732 = 43.3 Amp

Let the capacitor of C capacitance is connected in parallel with motor then,

New Power Factor = 0.9,

cos Φ_{1} = 0.9,

tan Φ_{1}= 0.4843

New reactive component = I tanΦ_{1} = 25 * 0.4843 = 12.1 Amp,

Thus, current through capacitor = 43.3 - 12.1 = 31.2 Amp,

As we know,

C = 451 * 10^{-6} F

Here is a Numerical Problem : -

A single phase 220 volts, 50 Hz, motor takes a supply current of 50 Amperes at a power factor of 0.5 lagging. The motor power factor has been improved to 0.9 lagging by connecting a condenser in parallel. Calculate the capacitance of the capacitor required ?

Solution : -

Please note that current power factor is 0.5 it indicates that motor is induction motor or an inductive load is connected to the system.Data extracted from above problem : -

Motor Type : - 1 Phase, Induction Motor,

Voltage Applied : - 220 volts,

Current from Supply : - 50 Amp,

Supply Frequency : - 50 Hz,

Current Power Factor =cos Φ=0.5 ( lagging ),

Φ = cos

Active Component of current, say I

One thing you must remember regarding power factor improvement

` Improving power factor does not change active power consumed in the appliance. `

Since the voltage also same so only current will be changed after power factor improvement. Hence only total current will be changed but active component will be same i.e. 25 Amp.

Tan Φ = tan 60 = 1.732,

Reactive component of current, say I

Let the capacitor of C capacitance is connected in parallel with motor then,

New Power Factor = 0.9,

cos Φ

tan Φ

New reactive component = I tanΦ

Thus, current through capacitor = 43.3 - 12.1 = 31.2 Amp,

As we know,

`I`_{c} = V/X_{c} = 2*pi*f*C*V

C = 451 * 10

Article Was Last Updated on **Saturday, March 10th, 2018 At 12:57:15 pm**

Follow steps described here at your own risk. Privacy Policy

Impossible is a word to be found only in the dictionary of fools.

Articles: 46

Viewed: 237384 Times

Photos : 53

Viewed: 515792 Times

Questions : 2344

Viewed: 137818 Times

Page Load No. 1036811

Photos

Take Quiz

1 Liners For Exam

Show Questions(1 by 1)

© 2011-2018 @ www.SunilSaharan.in